The corrosion and scale inhibitor currently on the market is the long-term use of water treatment chemicals. They are more expensive. It ranges from 5,000 yuan to 20,000 yuan per ton. This puts a heavy economic burden on water treatment companies that use corrosion and scale inhibitors.
In order to enable customers to use corrosion and scale inhibitors efficiently, let’s share the method of saving the use of slow release scale inhibitors.
Method one. According to the test parameters of water, the corrosion and scale inhibitors are used in a targeted manner.
If the water quality of the circulating water can be tested, then the corrosion and scale inhibitors should be used according to the test results. In this case, it reduces a lot of unnecessary waste. In addition, it can bring good economic benefits to customers. Therefore, it is best for qualified customers to test the water quality in a targeted manner.
Method Two. Corrosion and scale inhibitor blending.
If there is not much material in the water, it can be blended according to the situation. The ratio of corrosion and scale inhibitor blending should not be too large. Generally controlled within a ratio of 1:1. If there is too much blending, the dilution of the corrosion and scale inhibitor will be lost. Thereby reducing the function of the corrosion and scale inhibitor.
Corrosion and scale inhibitors are a kind of products with better water treatment effect. Mainly used in the water treatment industry in various fields. However, many people do not use corrosion and scale inhibitors effectively. In most cases, the unsatisfactory result is not due to the poor quality of the corrosion and scale inhibitor products. Today IRO water researchers analyze the causes of the effects of corrosion and scale inhibitors.
The most influential reason should be the method used. Many people will add sewage themselves when they use it. Do not follow the above requirements in the instruction manual. This will definitely affect the effect of descaling. If you add less, it will definitely not be clean, but if you add too much, it will probably chemically react to water quality.
It is recommended that you check the instructions in the instructions before using, and understand the concentration of the ratio and then proceed with the treatment. Only after re-understanding the basic situation of corrosion and scale inhibitors can the effect be better.
I suggest you check the instructions before using. After understanding the concentration of the ratio, it is processed. Only by re-understanding the basic situation of corrosion and scale inhibitors can the effect be better.
The second is the problem of water treatment chemical addition.
The addition of a water treatment chemical plays an important role in the operational stability of the reverse osmosis membrane system. The right addition can make the most of it.
1. When adding water to the metering tank, be careful not to exceed the maximum liquid level.
2. The initial addition of the water treatment chemical should first clear the addition box. Close the bottom drain valve of the metering box when cleaning. After the water is cleaned, open the drain valve to drain the water. After two passes, the amount began to increase.
It is important to note that the motor is stopped after the water treatment chemical is evenly stirred. At the same time, open the metering pump inlet and outlet valves and open the metering pump switch. The pharmacy is added before the security filter. After the RO stops running, the metering pump is turned off.
3. Adjust the metering and adding a stroke. Turn the metering stroke adjustment knob counterclockwise to the corresponding scale. Also, pay attention to the water treatment chemical. Check that the drain valve at the bottom of the metering tank is closed. According to the effective volume in the metering box and the actual working output of the metering pump. Add the agent from the inlet of the metering box. Open the inlet valve and dilute to the highest level mark and close the makeup valve.
4. Record water treatment chemicals every month. Check whether the total water intake and the amount of the matching period match, and regularly check the filling system for leaks, and promptly resolve the leak.
The performance of water treatment chemicals configured by different manufacturers may be different, so users should purchase water treatment chemicals according to actual needs.